Find great deals for Gamewell Flex If LCD Display With CPU Fire Alarm Board ASSY If Shop with confidence on eBay!. The Gamewell Retrofit Kits offered by Gamewell-FCI provide a simple way to convert without replacing the existing Gamewell backbox. IF panel. Gamewell IdentiFlex Fire Alarm Control Panel. FIRE ALARM AND SMOKE DETECTION SYSTEM. 1. GENERAL. RELATED DOCUMENTS.
|Published (Last):||23 August 2010|
|PDF File Size:||3.48 Mb|
|ePub File Size:||20.31 Mb|
|Price:||Free* [*Free Regsitration Required]|
With care and maintanence, commercial grade smokes last a long time, but a facility like a school is a pretty hard use environment. Gamewell has been around forever, I’ve seen some really old systems by them ic610 are probably obsolete. Mon Sep 22, 5: The GW is a good panel. We have literally hundreds of customers that have older gamewell systems in them.
Wed Sep 24, 6: Gamewell IF heat detector false alarms Posted: The fire alarm company who was “maintaining” the system for the last 5 years of course does not know anything about this?
Any advice would be greatly appreciated. Heat detectors associated with elevator control should always be fixed temperature only, not ROR, in order to activate prior to the sprinkler head.
The E3 can be a direct replacement for the 6oo series GW panels.
That being said, what temperature rating sprinklers are installed? They merged under the Honeywell umbrella.
Gamewell Flex If610 LCD Display With CPU Fire Alarm Board ASSY 30867 If600 71804
The cost on parts for the is NOT going to go down but rather UP gameweell parts become less and less available. Ggamewell 13, I don’t know if they’re still in business as the company making the city master fire alarm boxes but the fire alarm panel line became Gamewell-FCi and then got swallowed agmewell into the Honeywell cluster.
Would anyone happen to know if just like with the Notifier systems, that system points in the IF may just go bad??? IF that is the case, then would anyone happen to have the software that I need to change the device address and the related functions in the program?? The ambient temperature is fairly warm though far from hot enough to cause a legitimate alarm condition. I am also being told that all of our detectors need to be replaced as they are almost 10 years old and past their life expectancy.
Did you miss your activation email?
SMF – Just Installed! January 15, This card is made to run the older Gamewell Apollo XP95 devices. Please login or register. This works great too. You cannot post new topics in this forum You cannot reply to topics in this forum You cannot edit your posts in this forum You cannot delete your posts in this forum You cannot post attachments in this forum. You get the picture. Recently, UL updated it’s fire alarm standards from 8th edition to 9th edition.
Now there is ventilation provided by an exhaust fan and two open-air elctro-mechanical dampers, all of which are open and running. Most of the fire alarm builders have sunseted their older models, as a result. The company I work for has been with Gamewell for over 40 years. January 16, Yes this really happened to me a few months ago.
If you have any Q’s let me know. Hello everyone, I’ve exhausted all of my outside resources now troubleshooting the cause of false alarms from a XPT addressable heat detector on an IF system.
Logged The Truth of Thermodynamics: Further, the rate of rise is consistent with the second tower on the property, which is not having this issue. Page 1 of 1.
Gamewell If GW Bus Driver Signal System Control Module | eBay
Real Knowledge From Real People. Anyone who tells you all their jobs are perfect is full of SH1t. Previous topic Next topic. The location is inside the elevator machine room on the roof top of a 10 story tower in Long Beach.